Backup of small hydroelectric powerstations
Gensets for backuping powerplants in Bešeňová and Dubnica nad Váhom
Two gensets MP 30 B with power 35 kVA for backuping small water powerplant. Genset in Bešeňová is open genset situated in engine room. Genset in Dubnica nad Váhom is in weatherproof canopy situated outside.
Gensets for SEPS
Container gensets for Slovak electricity transmission system in combination with UPS sources
SEPS Bratislava – Container genset MP 640 O with automatic starting for supply of the main building and data center of SEPS in combination with 3 x 250 kVA UPS in container.
SEPS Rimavská Sobota – Container genser MP 300 I for substation supply.
Compressor station Nea Messimvria, Greece
Backup generator of compressor station
Genset MP 1000 P with power of 1000 kVA in container. Air inlet and outlet are through electric louvers. Residential silencer with noise reduction -30 dB is on the roof of container. Fuel tank with volume of 5000 l with gear pump for refilling ensures continuous 24 hour operation. Container is equipped with automatic fire extinguishing system.
Thermal power plant Orapa, Botswana
Genset in container for starting of the thermal power plant
Genset MP 1000 P with power 1030 kVA fitted into 30′ container. Genset is intended for suppliing power during starting procedures of thermal power plant near city Orapa in Botswana. 1800 l fuel tank with filling from outside is fitted in container. Container was certified for sea transport because of transport to the installation place. Residential silencer mounted on the roof of the container is composed of two parts and during transport was placed inside the container, next to genset and fuel tank.
Power plant Yunus Emre, Turkey
Biggest genset produced so far
MP 2250 M with 2250 kVA power produced and installed in thermal powerplant Yunus Emre in Turkey. Genset is installed inside of the insulated container with external cooling system on the roof. Whole genset is designed for backup emergency cooling of the powerplant during blackout or fault.